Water supply, sewage and waste disposal.
The licensee must ensure that water supply and waste disposal in each facility meet the provisions of chapter 246-290
WAC, whichever applies, including:
(1) Maintaining tempered water between one hundred and one hundred twenty degrees Fahrenheit in resident areas.
(2) Maintaining the plumbing systems free of cross connections.
(3) Assuring all sewage and waste water drain into a public sewer system in compliance with applicable laws and rules, or meet the requirements of chapters 246-272
WAC, and local laws and rules.
[Statutory Authority: Chapter 71.12
RCW. WSR 05-15-157, § 246-337-130, filed 7/20/05, effective 8/20/05.]